CIP Program Steps
Use inner vertical slider to view all text in scroll box.
On completion of the Caustic wash the circuit will be drained by pressing F10 DRAIN CIRCUIT.
This action will (a)stop the CIP Pump, (b) open the DRAIN Valve (V04), and (c) close the RETURN (Recycle) valve V03.
In most commercial applications of automated CIP and AIR BLOW will be initiated to clear the CIPS line of solution. The “state-of-the-art” Mini-CIP Skid has that capability but the circuit lacks the robust construction required to handle the introduction of air.